Written on: January 1, 2020 by George Carey
Waste not, want not. This expression dates back to around 1772 and it basically means if you don’t waste something you will never have a want for it. And those who waste will want. Waste and want or save and have. When it comes to heating systems, you don’t want to create a system that uses the fuel source inefficiently.Waste not, want not!
Over the years I have seen several systems that violate this principle. With energy costs on everybody’s radar screen, it is in your best interest to provide or improve your customer’s existing hot water to minimize their waste. There are several steps that you can take to eliminate wasted energy in a heating system. This includes two very obvious ones, which have little to do with the actual heating system:
1. Increase the insulation in a home and
2. Upgrade the windows (whatever heat the system produces—keep it inside the building for as long as possible).
Regarding the heating system, short-cycling is a major efficiency killer. It strikes in multiple areas, including mechanically and economically.
The mechanical problems occur because of the rapid cycling on-and-off of the boiler. All of the various components found on an oil-fired boiler have an expected life cycle. When a boiler is short-cycling, the components are seeing all these cycles in a very short time span.
This leads to premature control failures, nuisance lock-outs, service calls and frustrated customers. If you want to kill a brand new boiler in less than five years and frustrate yourself and your customers along the way…short-cycle it!
The economical problem is often unknown and is certainly under-appreciated. There is an old rule-of-thumb that states: A short-cycling boiler will operate at least 15% points below its rated efficiency when said boiler is not short-cycling. The loss of fuel efficiency can be staggering, which means the wasted fuel consumption is paid for by the unsuspecting homeowner with the new high-efficiency boiler.
So if you want to prevent short-cycling, what can you do? The first step is to ensure that the boiler is not oversized. When a boiler is too big, it will always produce more energy (BTUs) than the system can receive/use (without overheating the space). By being too big it reaches its high limit very fast, not allowing the boiler/burner to operate in a “steady state fashion.”
The best way to make sure that a new boiler is not too big is to perform an accurate heat loss assessment on the house. There are several software-based heat loss programs available that will help you establish the heat loss of any building. By using this information you can then select the right size boiler for the house instead of relying on someone who came before you and installed the previous, and perhaps wrong-sized, boiler.
Unfortunately, no good deed goes unpunished. A boiler can still short-cycle even when it is sized properly. Do you know why? Load and zoning are the reasons. A properly sized boiler is sized for design conditions. This means that when it is very cold outside (design outdoor temperatures), the boiler is capable of keeping the occupants at design indoor temperatures which is usually around 70°F. However, these outdoor design conditions exist for less than 5% of the total heating season, which means for the remainder of the heating season, even the properly sized boiler is too big and can lead to short-cycling.
Hydronic systems and zones
An advantage and/or selling feature of a hydronic system is that it can be zoned very easily. Most homeowners like the idea of being able to control sections of their house even right down to a room-by-room control. This unfortunately can also lead to short-cycling.
If one or two small zones are calling and the boiler fires in response, the energy output of the boiler is greater than the needs of the smaller zones. The high limit is reached very rapidly and the boiler shuts off. The zones continue to call and the water temperature drops. The limit control responds and the boiler fires up again. Of course, the high limit is reached quickly and the boiler turns off. So even though the hydronics industry promotes its zoning capabilities and homeowners enjoy the comfort and control offered by zoning, it can really foul up the boiler’s potential efficiency rating.